Demineralization or Deionization is the process of removing mineral salts from water by using the ion exchange process. With most natural water sources it is possible to use Demineralisation and produce water of a higher quality than conventional distillation. Fluid Systems Manufacture a Wide range of custom-built softening, Demineralizing plants for industrial process water applications, with inherent design to conserve water, and save cost.
We manufacture and export a wide range of DM Plants that are extensively used in various industries. Widely known for its weather resistance and leak proof ability, our products can be customized as per the specific demands of our clients. We also provide installation training, operation training and onsite support for our DM plants.
The demineralization process utilises acid regenerated cation resin & caustic regenerated anion resin to remove minerals from water. Trolly mounted automatic operation DM Plants are also available for small industries and laboratories.
DM Plants are available in a wide range with max flow rate from 10 Ltrs/hr to 250000 Ltrs/h in standard plants.
Applications: Easy to install, Simple to operate, Complete with regeneration equipment & control .
For best distilled quality water without heat & electricity. Mainly uses in Pharmaceutical industries. Chemical Industries. Mirror Silvering, Power Stations, Research Labs, Food Processing, College Labs, Plastic Industries.
Two Ion exchange MSRL / FRP shell, one is Cation Exchanger and other is Anion Exchange fitted with MSRL / PVC pipe lines, valves, strainers and filled up with Cation and Anion Exchange Resigns and containing Acid and Alkali proof pots for regeneration.
In the simplest system the raw water flows successful through a Cation Exchanger regenerated with acid an Anion Exchanger regenerated with caustic soda. When the raw water passes through Cation Exchanger all the Cations are retained by the resin and there is no longer anything in the water but the acids of the salts it contained initially. Then the water passes through Anion Exchanger which absorbs the Acids and thus the D.M water is produced.
QUALITY OF D.M WATER
Purified water as per I.P conductivity -1 to 20 micro ohms/cm
pH of D.M water : Around 7.0 Storage Battery : IS : 1069 / 64
CAPACITY FLOW RATE
| VESSEL SIZE
DIA HT. VOL.LTR.
|VALVE & PIPE LINE
|AT/SFT/250||250||FRP||200 880 27||20||½” M.P.V.|
|AT/SFT/500||500||FRP||200 880 27||20||¾” M.P.V.|
|AT/SFT/700||700||FRP||254 1371 63||50||¾” M.P.V.|
|AT/SFT/1000||1000||FRP||355 1220 150||75||¾” M.P.V.|
|AT/SFT/1200||1200||FRP||355 1372 150||100||¾” M.P.V.|
|AT/SFT/1500||1500||FRP||355 1650 150||125||¾” M.P.V.|
|AT/SFT/2000||2000||FRP||457 1650 236||150||¾” M.P.V.|
|AT/SFT/2500||2500||FRP||457 1650 236||200|